VAS provides ideal solutions to broadcast evacuation messages, announcements and background music in a broad variety of
environments: schools, hotels, shopping centres, supermarkets, recreational facilities, factories, offices and other similar applications where public safety is of the essence.
Continuous control of the entire system
One big step towards a sound investment
COMPACT, EXPANDABLE AND SECURE SYSTEM
Designed as a versatile solution, this system is easily configured for specific applications.
It is available in 2 versions, VAS 8 and VAS 16M/S.
The Master module (VAS 16M) can be used on its own or cascaded with one or several slave modules (VAS 16S).
Assembling these modules helps extend system capacity up to 40 broadcast zones, 40 Alarm zones and 80 speaker lines which can be selected via the MAG-80 microphone console (1 Master and 9 Slaves).
The VAS-LINE station cascaded with the VAS16 M/S makes it possible to add up to 16 extra speaker lines.
Message heard, greater safety
Designed to easily broadcast announcement and emergency messages, VAS guarantees an autonomous, ready-to-use concept, ideal for small and medium-sized applications.
NO COMPROMISE ON SECURITY
VAS meets all the stringent functionality and emergency requirements in case of failure set by the EN 54-16 standard on
These prevention and safety measures include system supervision, switch to the backup amplifier, monitoring of speaker lines, an integrated message player and exhaustive commands and displays on the front panel.
VAS system component : unrestricted configuration
INPUTS - OUTPUTS
Each station can manage 4 Alarm Zones (40 in total for a 10-station VAS 16 system).
4 Music Inputs and 2 AUX inputs.
1 General Calling Console Input (MAGPL-D). Unlimited number of consoles, all in parallel.
1 Selective Calling Console Input (MAGPX 4). Unlimited number of consoles, all in parallel.
1 Selective Calling Console Input (MAG 80). maximum of 8 consoles (in parallel).
1 Safety Microphone Console Input (MAGS).
1 Safety Microphone Console Input (MAGS-FP).
1 Monitored message player capable of broadcasting 4 evacuation and pre-alert messages.
1 message player capable of broadcasting 2 messages directly from an embedded SD card.
4 Normally Open Dry Contacts (1 for each Alarm Zone) to trigger evacuation. This link is controlled from the station in open/short circuit and Grounded by scanning a resistance.
4 UGA (Alarm Management Units) inputs to trigger evacuationover a voltage of 24V to 60vDC (via VAS-INT-UGA CARD).
4 x 0dB unbalanced outputs on RCA connector (to amplifier links).
1 x 0dB unbalanced output on RCA connector (to backup amplifier link).
16 x 100V line HP outputs (A/B).
1 general default synthesis output (D.C*) on each station.
1 x 220vAC and 24vDC power failure signal output (D.C*).
1 event programming signal output (D.C*).
1 RS232 port for connection to PC (system configuration).
1 RJ45 port to cascade the stations.
220vAC power supply.
24vDC power supply.
Priority level: Safety Mic 1 > Safety Mic 2 > Alarm1 > Alarm 2 > Alarm 3 > Alarm 4 > Aux 1 > Mess 1 > Selective calling consoles > Aux 2 > Mess 2 > Music 1 to 4.
Settings (DSP): Volume of each source in each broadcast zone, Master Volume for each broadcast zone, Bass/Treble for each broadcast zone.
We are very familiar with your environments and constraints.
This is why we can provide you with a smart system, designed to respond to an infinite number of
existing and potential situations.